We recommend rigid duct for maximum efficiency, health benefits and durability. To ensure maximum heat recovery and virtually silent operation, high quality thermal insulation and acoustic duct is used. In limited spaces such as ceiling voids or barn conversions, where there is exposed roof structure, special low-profile duct can be specified. The ductwork can usually be hidden quite easily around the house.
For an installation manual, please visit our downloads section.
This is normally an area where you can run the ductwork freely from the Genvex appliance to the ceiling terminals in the ceiling of the floor below (usually the first floor). The duct is usually at a 200mm/250mm diameter at this stage coming straight off the appliance and it will reduce down to 100mm/125mm to be connected to the ceiling terminals.
If you are using the loft as habitable space as well, hopefully there will be some dead space created on either side, by the pitch of the roof. Check the specification of the Genvex appliance that you think is suitable for your property, to work out the minimum space required. For access to clean the filters, it will be best to leave approximately 600mm in front of the appliance, or integrate an access door within the wall so that the appliance remains accessible.
Alternative locations for the appliance can be in large cupboards or perhaps in your utility or plant room â€" the loft area is just the most convenient.
Although your Genvex appliance runs pretty much silently, you will usually locate it above a bathroom or dressing room, to minimise the risk of noise caused by vibration. The Genvex appliance should be mounted on plenty of insulation on top of the joists, or on the wall. The appliances weigh between 40-225kg, but it is best to check the specification sheet for the exact weight of the appliance, to ensure the surface it is to be mounted on, will have a satisfactory weight-bearing capacity.
The appliance will produce approximately 3-5 litres of moisture in the winter months, so you will need to fit a condensate pipe to a trap linked to your internal waste water pipe.
You need to be aware of where you can locate the two louvres, for the fresh-air intake and stale-air outtake. These need to be placed a MINIMUM of 3m apart horizontally or 1m apart vertically to stop cross-contamination. They can be located on the gable end of the loft area, under the eaves or you can have special roof vents which your roofing contractor can supply you with.
Will the property have a warm roof or a cold roof? This is very important to establish with your architect or builder before we complete a quote for you, as it will effect the insulation properties of the ductwork in the loft.
A warm roof is where the insulation is placed in the roof itself, therefore making the roof area warm. If insulation is only going to be placed in the floor of the loft area, this is known as a cold roof as the loft area will be cold in comparison to the rest of the house.
If you have a cold roof construction the extracted air ducts from kitchens and bathrooms and the supply air ducts to the habitable rooms of the house will need to be well insulated where they are in the loft area. This will obviously increase the cost of the quotation so that more insulation can be accounted for.
Rigid metal ventilation ductwork
In the ceiling voids, you will mainly have to run the ductwork with the joists, unless of course your floor construction allows for ductwork to go through it, ie posi joists. Always check with your builder or surveyor before making holes through any joist structure.
PVC flat channel ventilation ductwork
To drop down to the lower floors you can utilise the following spaces:
- soil-pipe boxing or existing boxing-in
- boiler cupboard
- fitted wardrobe
- coats cupboard
Flexible ventilation ductwork
The ideal place for locating ceiling terminals is opposite a door but next to a window, so you create air circulation. Of course when you get downstairs or to the lower floors, you are more restricted on where you can put the terminals, as you will be channelled by your route.
Most of the time, the terminals downstairs are likely to be at the corners of the room where the voids to drop the ductwork down, are likely to be above.
Occasionally you can use low profile duct to drop down a timber partition, but for airflow purposes, it is best to restrict the use of this flat channel ducting as much as possible.
To view our Genvex Pricelist, please visit our downloads section.
The Genvex appliance itself would normally need to be wired into your house electrics by a qualified electrician, although if you have an electrical socket nearby you may be able to just plug in there. It will be best to speak to your electrician first.
The controller should be placed in a hallway or landing where you will have convenient access to alter the program or put the system on boost. Low voltage cable needs to run from the controller to the Genvex appliance.
To view the Optima Controller User Manual, please visit our downloads section.